- Service air conditioner. Check condition of all belts and lines. Evacuate and recharge with reclaimed R-134. Test system performance. Inspected and found high side shredder valve is leaking. Replaced valve at no charge to customer and confirmed proper operation. Before: High _148_, Low_18_, Ambient temp_80_ Duct temp_L-85* R- 60*_. After: High __125_, Low_38_, Ambient temp_85_ Duct temp_41__.
- Replace serivce ports.
Ione S. gave our service a 5 star review on 7/12/2022